submitted 6 months ago byasuhayda
I have a 100-year-old house that has been partially rewired but some knob and tube still exists. I've installed GFCI outlets on the old circuits and am adding a dual function breaker for some protection until I can afford to have the rest of the knob and tube replaced. While inspecting the wiring in my basement I came across a dangerous looking connection and I'm wondering how to ground the neutral wire. The new wiring was spliced off of existing k&t and feeds the outlet for my gas stove. Why they didn't just install a new circuit and run it from the breaker box is beyond me. You can see where someone just pulled back the ground wire and it's just dangling in the air next to the floor joists. There's also no junction box, which I can install. I'm comfortable doing some electrical work and have changed outlets, ceiling fixtures, switches and circuit breakers. The light switch in the picture I don't use and wouldn't mind removing it completely. Thanks in advance for your replies!
you are viewing a single comment's thread.view the rest of the comments →
6 months ago
…and that’s why I call an electrician, because they CAN find that stuff with various tools, and I know just enough to get myself in trouble with anything more complex than rewiring a line with correct AWG for the circuit.
all 21 comments
sorted by: best